A blend of R-22 and R-125 with hydrocarbon R-290 (propane) included to improve mineral oil compatibility. This blend is formulated to match R-502 in evaporator temperature ranges and does not significantly increase discharge temperature in R-502 retrofit situations. Discharge pressure, however, can increase from 25 to 40 psi over pressures seen with R-502. Although the propane was added to improve oil circulation, it is still recommended that some mineral oil be removed and replaced with alkylbenzene.
|27R402A||27 LB. CYLINDER|
|110R402A||110 LB. RETURNABLE CYL.|
Download SDS for R-402A.
Download the R-402A product information
from the NRI Refrigerant Reference Guide